Exterior insulation status of our building must be controlled and all necessary insulation has to be made. For room temperature control, required comfortable temperature is fixed by thermostatic radiator valves. Moreover, intended instant temperatures are attained via room thermostats by temperature and program adjustment. The front side of radiators should not be blocked with seats and laundry to be dried shouldn’t be placed at the top.
Ideal water pressure value seen at the water pressure manometer on the Wall Hung Boiler has to be between 1-1,5 bars. When pressure drops, please add water to the tank by using the filling valve nearby the manometer until reaching the ideal water pressure. Be sure that the valve is close-fitting after the process.
For periodical maintenance of the Boiler, we suggest minimum one maintenance per year which is to be carried out either before or after the winter season.
This varies due according to the current status of your device. However, it would take approximately 45-60 minutes.
Controlling flue connections
Gas leak control by U-manometer (Next to the Boiler gas feed line)
Electrical controls and measurements
Controlling the system water pressure and deairing the installation if necessary
Asking the customer for any complaints about the device already under usage
Sweeping the fan or fume hood funnel
Purification of the air-ducts of the funnel
External refinement of general equipment
Controlling capacity settings
Cleaning installation filters
Control and purification of the bottom hydraulic group
Control and purification of the circulation pump
Control and external refinement of the main exchanger
Controlling air pressure of the expansion tank
Oxidation cleaning of the general equipment
Condensate drainage line control
Instalment water input pressure control
Controlling gas pressure values
Controlling general operating functions of the product
For periodical maintenance of the Air Conditioner, we suggest minimum one maintenance per year which is to be carried out either before or after the summer season.
This varies according to the current status of your device. However, it would take approximately 60 - 90 minutes.
Internal Unit evaporator cleaning
Internal Unit filter cleaning
Internal Unit fan cleaning
Lubrication of the Internal Unit fan bearings
Cleaning Internal Unit water outlet canal
Internal Unit gas sealing control
External Unit condenser cleaning
External Unit fan cleaning
External Unit electrical connections control
External Unit gas leakage control
Remote control performance check
Device running test
Control of device gas pressure values
Control of the brackets and all unions of the device
Building electric voltage value control
Draw current of the compressor at device start-up
Device blow value control by thermometer
Control of device sound index
Heat pumps are devices which transfer the ambient heat from current environment to another with external energy supply. Using heat pump products enables space heating, space cooling, pool water heating/cooling and domestic hot water procuring. Heat pumps consume little energy due to the cooling cycle principle and natural energy is used as the heating source.
Using a heat pump products enables space heating, space cooling, pool water heating/cooling and domestic hot water procuring. Minimum Energy Consumer and Cost-Efficient Baymak heat pumps provide energy conservation in flats, buildings, pools and several impositions thanks to low energy consumption. Devices also reduce operating cost due to low energy consumption.
Baymak heat pump coefficient of performance (COP) achieves as much as 4,6 due to its operation principle. By this means, 1 unit energy input to the system produces an output proportional to COP value, enhancing more unit energy amounts. Minimum Energy Consuming and Cost-Efficient Baymak heat pumps provide energy conservation in flats, buildings, pools and several impositions thanks to low energy consumption. Devices also reduce operating costs due to low energy consumption. Heat pumps run in all weather conditions without being affected, and temperature is the only aspect substantial for the devices. Heat pumps are usable in any weather condition regardless of snow, rain or sun.
Yes. Using heat pump products enables space heating, space cooling, pool water heating/cooling and domestic hot water procuring.
Any electricity subscriber having the suitable space can draw on PV systems.
PV systems are applicable to all roof types. However, roofs avoiding shadow are preferred and the northward side of inclined roofs are refrained considering power generation performance.
Baymak package systems do not operate in locations having no electricity due to the fact that they are not able to run without a network connection. Likewise, they do not act as an alternative energy source during electric cut-outs. Grid-tie systems are only used for fulfilling the need of mitigating available energy demand.
Adding up all the equipment, the system charges maximum 20 kg/m2 load on the roof.
When generated electricity is inadequate for your needs, the lacking part is taken from the network requiring no intervention.
Uygun alana sahip her elektrik abonesi PV sistemlerden yararlanabilir.
All necessary actions enabling the system to function properly are performed by a team of specialists. All obligatory legal procedures determined by the state for installation are implemented by us. The products are available in any location of the country thanks to our prevalent Turkey-wide dealer network, and installed by a team of experts under the Baymak guarantee. The authorized technical service enables responsive solutions to any problem that can rise after the installation.